The UK like many other countries is experiencing an energy revolution. Energy storage is seen as one technology that can help countries to meet their energy demand needs, low carbon and climate change obligations. Storing energy for later use is a growing industry with expert reports proposing 5-year compound growth figures of over 22% for the domestic market alone.
There are several technologies available ranging from pumped-hydro to flow batteries and compressed air storage in underground caverns at the grid level, to the use of local energy storage (LES) systems within commercial and residential properties. The role of an LES is very similar to that of an uninterruptible power supply but in a primary or ‘active’ role rather than a secondary ‘standby’ one.
Within datacentre and server room environments there is a growing interest in how best to apply energy storage alongside UPS systems. There is still the need for protection from local power outages, but the emphasis is more on how to:
The most common battery type for energy storage applications is a Lithium-ion (Li-ion) or Lithium Polymer battery. These are more suited to this type of primary application than lead-acid batteries due to the more rapid and frequent charge/discharge cycles required from the battery set. Lead acid batteries are more suited to standby cycles and in for renewable applications lead acid OPzS batteries are the preferred choice if a lead acid battery is specified.
Energy storage systems can act as a virtual power plant where the energy storage during off-peak periods or from renewable power sources, can be used as the primary source when mains power is available but at peak-rates. The difference in electricity kWh costs can be used to recover the spend on the capital investment. This type of arrangement could benefit domestic as well as some commercial properties.
For datacentre operators a virtual power plant arrangement provides the option for the facility to become more grid independent. The stored energy could be used to support a UPS system and reduce the need to run on local standby power generators which are typically diesel powered. In addition the stored energy could allow the site to take part in a National Grid demand side response type program or feed-in-tariff arrangement.
Demand side response programs are aimed at balancing demand on the grid and maintaining the frequency within set tolerances to the National Grid to avoid Ofgem penalties. As part of a DSR program, a datacentre could agree to disconnect itself from the grid for a set period thereby removing potentially demand for up to several hundred kilowatts or megawatts of power from the grid. Stored energy could also be exported back to the grid in much the same way as wind turbine and solar PV plants operate.
The way to size and select batteries for use in energy storage systems is much the same as that for an uninterruptible power supply. There are common steps but with some that are more specific to the rapid charge and discharge cycles for energy storage systems:
A UPS system is designed for use with a specific battery type, whether this is lead acid or lithium. There is no dual-source UPS system currently available. This means a decision as to which battery technology is right for the application must be taken at the project design stage.
Most UPS suppliers and manufacturers now include lithium-ion powered uninterruptible power supply alternatives. Small single-phase UPS systems using lithium-ion batteries are more suited to remote Edge computing and higher temperature server rooms applications. The UPS are more compact due to a higher power density than lead acid batteries and higher temperature tolerant. For larger three-phase monoblock or modular UPS applications including use as virtual power plants, the lithium-ion batteries are supplied as a separate battery cabinet system including the battery monitoring and management system.
UPS systems have always stored energy for later usage. The difference between this type of arrangement and that of a local energy storage system is that the charge/discharge cycles are more frequent and the wider applications available including taking part in grid balancing roles. Within the next five years lithium-ion will become the dominant battery choice over lead acid for datacentre and server room backup power applications. This will then give operators the choice as to how they configure their UPS. Whether as a standby power source for emergency protection from power outages or in a more proactive energy storage role.
Ever since the UK Government introduce the feed-in-tariff (FIT) for solar PV and wind turbine installations, one of the biggest challenges has been how to store the generated energy for later use. Lead acid batteries have limited capabilities when it comes to frequent energy storage and discharge cycles and are more suited to standby power applications. Applications including electric vehicles and mobile computing applications also required an energy storage mechanism that could cope with rapid charge/recharge cycles and offer a longer working life. Lithium-ion batteries have rapidly become the energy storage device for these applications and are slowly being adopted into UPS system applications.
Micro grid technologies were originally designed to allow sites to become grid independent. A typical site has a solar PV or wind turbine installation, some form of battery to store the locally generated energy and an inverter to convert the stored DC energy into an AC supply for the connected loads. The site may also have a local diesel standby power generator. This type of energy storage arrangement is one that can benefit both datacentre and national grid operators.